2-3. LOCATION AND USE OF CONTROLS AND INDICATORS (CONT).
Figure 2-1. Generator Set DC Instrument Panel Controls and Indicators (Cont).
Control or Indicator
Indicates the battery charging system voltage. Normal
charging voltage is 22 to 28 volts.
Starts and stops the generator set locally.
Running Time Meter
Registers the total number of hours the unit has run. Use it
to keep a record of periodic servicing. Time is cumulative;
meter cannot be reset.
Reset/Lamp Test/Panel Lamp Switch
Resets the fault circuit only when the Run/Stop/Remote
switch is in the Stop (Reset) position. Tests fault lamps and
turns on the control panel lamp.