Dry cleaning solvent is flammable. Do not use near open flame or non-
ventilated places. Keep solvent away from open flames or sparks. Avoid
inhaling solvent fumes. Avoid contact with skin. Flash point of solvent is 100°
F to 138° F (38° C to 59° C).
DO NOT smoke when working with solvent
Thoroughly flush out fuel tank inlet (4) with dry-cleaning solvent.
Loosen knob (5) on bottom of fuel strainer (6) and remove glass bowl (7), gasket (8) and screen (9). Check
for loose sediments, or water. Empty glass bowl into appropriate container and clean inside of glass bowl
with dry-cleaning solvent
Make sure that gasket lies flat around rim of glass bowl and inside lip of fuel
Place screen (9) and gasket (8) around rim of glass bowl (7) and install into bottom of fuel strainer (6).
Tighten knob (5) until a snug fit between knob and glass bowl (7) is accomplished.
Install fuel hose (3) and clamp (2) onto fuel tank inlet (4) Tighten clamp (2).
Check for leaks; repeat procedures if necessary
Replace pipe cap (1) onto bottom of fuel tank.